STEAM TURBINE COMPONENTS
1.) Turbine casing (HP, IP and LP Turbine Casing)
2.) Anchor Points of Turbine
3.) Rotor (HP, IP and LP Turbine)
5.) Sealing system (Gland Seal, Steam System)
6.) Bearings & Bearing Pedestal
7.) barring gear
8.) ESV’s, IV’s and CV’s
1.) Turbine Casings
HP Turbine Casing
Outer casing: a barrel-type without axial or radial flange.
Barrel-type casing suitable for quick startup and loading.
The inner casing— cylindrical , axially split.
The inner casing is attached in the horizontal and vertical planes in the barrel casing so that it can freely expand radially in all directions and axially from a fixed point (HP-inlet side).
IP Turbine Casing
The casing of the IP turbine is split horizontally and is of double-shell construction.
Both are axially split and A double flow inner casing is supported in the outer casing and carries the guide blades.
Provides opposed double flow in the two blade sections and compensates axial thrust.
Steam after reheating enters the inner casing from Top & Bottom.
LP Turbine Casing
The LP turbine casing consists of a double flow unit and has a triple shell welded casing.
The shells are axially split and of rigid welded construction.
The inner shell taking the first rows of guide blades, is attached kinematically in the middle shell.
Independent of the outer shell, the middle shell, is supported at four points on longitudinal beams.
Steam admitted to the LP turbine from the IP turbine flows into the inner casing from both side
2.) Anchor Point of Turbine
Purpose: Taking care of thermal expansions and contractions of the machine during thermal cycling.
The fixed points of the turbine are as follows:
The bearing housing between the IP and LP turbines.
The rear bearing housing of the IP turbine.
The longitudinal beam of the I.P turbine.
The thrust bearing in rear bearing casing of H.P turbine.
The HP rotor is machined from a single Cr-Mo-V steel forging with integral discs.
In all the moving wheels, balancing holes are machined to reduce the pressure difference across them, which results in reduction of axial thrust.
First stage has integral shrouds while other rows have shroudings, rivetted to the blades are periphery.
The IP rotor has seven discs integrally forged with rotor while last four discs are shrunk fit.
The shaft is made of high creep resisting Cr-Mo-V steel forging while the shrunk fit disc are machined from high strength nickel steel forgings.
Except the last two wheels, all other wheels have shrouding riveted at the tip of the blades. To adjust the frequency of the moving blades, lashing wires have been provided in some stages.
The LP rotor consists of shrunk fit discs a shaft.
The shaft is a forging of Cr-Mo-V steel while the discs are of high strength nickel steel forgings.
Blades are secured to the respective discs by riveted fork root fastening.
In all the stages lashing wires are providing to adjust the frequency of blades. In the last two rows satellite strips are provided at the leading edges of the blades to protect them against wet steam erosion.
most costly element of turbine
blades fixed in stationary part are called guide blades/nozzles and those fitted in moving part are called rotating/working blades.
blades have three main parts (1) Aerofoil: working part (2) Root (3) Shrouds
shroud are used to prevent steam leakage & to guide steam to next set of moving blades.
Three types of root arrangements are commonly used. They are (1) T-roots: for small blades; (2) Fir Tree or serrated roots – for longer blades; (3) Fork and Pin root: for longer blades shrunk on disc type rotors.
Integral shroud for are used for shorter blades and shrunk fitting for larger blades.
Lacing wires are also used to dampen the vibration and to match frequencies in the longer blades.
Since in the reaction type machine the pressure drop also occurs across the moving blades it is necessary to provide effective sealing at the blade tips.
5.) SEALING GLANDS
Steam is supplied to the sealing chamber at 1.03 to 1.05 Kg/sq.cm abs and at temperature 130 deg.C To 150 deg.C from the header.
Air steam mixture from the last sealing chamber is sucked out with the help of a special steam ejector to gland steam cooler
Provision has been made to supply live steam at the front sealing of H.P. and I.P. rotor to control the differential expansion, when rotor goes under contraction during a trip or sharp load reduction.
Bearings are usually forced lubricated and have provision for admission of jacking oil
6.A) Front Bearing Pedestal :- The Front Bearing Pedestal is located at the turbine side end of the turbine generator unit. Its function is to support the turbine casing and bear the turbine rotor. It houses the following components
b.Hydraulic turning gear
c.Main oil pump with hydraulic speed transducer
d.Electric speed transducer
e.Over speed trip
f.Shaft vibration pick-up
g.Bearing pedestal vibration pick-up
The bearing pedestal is aligned to the foundation by means of hexagon head screws that are screwed in to it at several points.
The space beneath the bearing pedestal is filled with non shrinking grout.
The bearing pedestal is anchored at to the foundation by means of anchor bolts.
The anchor bolt holes are filled with gravel,it gives a vibration damping effect.
Bearing Pedestal(HP Rear)
The Bearing pedestal(2) is located between the HP and IP turbine.
Its function is to support the turbine casing and bear the HP IP rotor.
It houses the following components
1.Combine Journal and Thrust bearing
2.Shaft vibration pick-up
3.Bearing pedestal vibration pick-up
4.Thrust Bearing trip(electrical)
Combined Journal and Thrust Brg.
The magnitude and direction of axial thrust of the turbine depends on the load condition
The Journal bearing is elliptical sleeve bearing.
The bearing liners are provided with a machined babbit face.
Located at each end of bearing shell, babbitted thrust bad forms 2 annular surfaces.
These collars and thrust pads permit equal loading of thrust bearing.
Thrust pads are of tilting type.
Metal temperature of the journal bearing and thrust pads is monitored by the thermocouples.
IP Rear Bearing Pedestal
Arrangement:The bearing pedestal is located between the HP and IP turbines. Its function is to support the turbine casing and bear the HP and IP turbine rotors. The bearing pedestal houses the following turbine components:
Shaft vibration pick-up
Bearing pedestal vibration pick-up
Hand barring arrangement
Differential expansion measurement device
27 thoughts on “Steam Turbine Components -Parts | Turbine Fundamentals and Basics | Basic Aspects of Steam Turbine Maintenance | Part#3 | Content-4 |”
You are a very smart person!
you are really a excellent webmaster. The web site loading velocity is amazing. It sort of feels that you are doing any distinctive trick. Furthermore, The contents are masterpiece. you’ve performed a excellent task in this topic!
whoah this weblog is great i really like studying your articles. Keep up the good work! You realize, a lot of individuals are hunting round for this info, you could aid them greatly.
Pretty nice post. I simply stumbled upon your blog and wanted to mention that I’ve really enjoyed surfing around your blog posts. In any case I will be subscribing for your rss feed and I’m hoping you write again soon!
Simply want to say your article is as surprising. The clarity in your post is simply excellent and i could assume you’re an expert on this subject. Fine with your permission let me to grab your feed to keep updated with forthcoming post. Thanks a million and please keep up the rewarding work.
Cool blog! Is your theme custom made or did you download it from somewhere? A theme like yours with a few simple adjustements would really make my blog shine. Please let me know where you got your design. Many thanks
It is in reality a nice and useful piece of information. I抦 satisfied that you shared this helpful info with us. Please keep us up to date like this. Thank you for sharing.
Valuable info. Lucky me I found your web site by accident, and I am shocked why this accident didn’t happened earlier! I bookmarked it.
I was just looking for this information for a while. After 6 hours of continuous Googleing, finally I got it in your web site. I wonder what is the lack of Google strategy that don’t rank this type of informative sites in top of the list. Normally the top sites are full of garbage.
Very good article! We will be linking to this particularly great article on our site. Keep up the great writing.
Thank you for sharing superb informations. Your web-site is so cool. I’m impressed by the details that you have on this blog. It reveals how nicely you perceive this subject. Bookmarked this web page, will come back for extra articles. You, my friend, ROCK! I found simply the information I already searched all over the place and simply couldn’t come across. What a great web-site.
We’re a bunch of volunteers and starting a new scheme in our community. Your web site offered us with valuable information to work on. You have done an impressive job and our whole community might be grateful to you.
You are a very bright person!
Greetings! Very helpful advice within this post! It’s the little changes that produce the largest changes. Many thanks for sharing!
This is a topic that is near to my heart… Cheers! Where are your contact details though?
Thank you for some other great article. Where else may anyone get that kind of information in such an ideal approach of writing? I’ve a presentation subsequent week, and I’m on the look for such info.
Very descriptive article, I liked that a lot. Will
there be a part 2?
Hello there, I found your blog via Google even as looking for a comparable subject, your web site came up, it appears to be like great. I’ve bookmarked it in my google bookmarks.
Wow, incredible weblog layout! How long have you ever been running a blog for? you make blogging look easy. The overall look of your site is fantastic, let alone the content material!!
Best view i have ever seen !
Best view i have ever seen !
Hello there! I could have sworn I’ve been to this blog before but after browsing through some of the post I realized it’s new to me. Anyways, I’m definitely delighted I found it and I’ll be bookmarking and checking back often!
Hey there would you mind letting me know which web host you’re utilizing?
I’ve loaded your blog in 3 different web browsers
and I must say this blog loads a lot quicker then most.
Can you suggest a good hosting provider at a honest price? Thanks, I
Wow, marvelous weblog format! How lengthy have you been blogging for?
you made running a blog look easy. The entire look of your website is fantastic,
let alone the content material!
Hello.This post was really fascinating, especially because I was investigating for thoughts on this subject last Monday.
cialis coupons Wearing elbow pads can also help protect the elbow bursa from pressure or additional irritation